The 19 "socket strips are in aluminum and polypropylene housings, the end covers are screwed or the strips can be reconnected.The strips are supplied with a connection cable and usually with a T12 or C14 plug.
Due to the design, the power strips can be mounted vertically and horizontally in the 19 "rack, on the rear panel or on the rack of the 19" network cabinet.
The C13 power strips are supplied in the following versions:
19 "PDU 9 x C13, inserts black, border black, white and orange, with T12 plug
19 "PDU 9 x C13, inserts black, border black, white and orange, with C14 plug
19 "PDU 12 x C13, inserts black, border black, with T12 plug
19 "PDU 9 x C13, inserts in black, border black, with T12 plug and ampere meter
Rated voltage: 230 V AC, 50/60 Hz
Rated current: 10 A
Rated power: P max. = 2500W
Connection cable: H05VV-F 3G 1.00 mm2, length: 3.0 m
Standards: IEC 60884-1
C13 / C14 - EN 60320-1
According to EN 60320-1, the device plug C14 and the device socket C13 are designed for a nominal current of 10 A, at a voltage of 250V ~.
T12 / C14 plug
C13 power strips are supplied with a T12 or C14 connector. Of course, alternatives are also possible, or the connection cable is assembled with an open end.